Jablotron 100 alarm system provides RS485 gateway to securely connect to 3rd party systems.
TapHome Core control unit provides 3 terminals for TapHome Bus devices, or other RS485-based devices. Thanks to support of Jablotron protocol, TapHome can read/write values from/to Jablotron 100 alarm.
Connect JA-121T with TapHome Core.
JA-121T provides galvanic isolation, therefore GNDs of Jablotron and TapHome power supplies should not be connected.
Open Settings → Hardware:
a. Disable Terminal 3 in TapHome Bus → Terminals
b. + Add new interface → Jablotron
Open Settings → Hardware → Jablotron:
a. Enable Terminal 3
b. Set Jablotron password (format 1*2345, where 1 is ID of external user, and 2345 is the password). This password must be created in Jablotron system.
Program PG outputs in Jablotron. In order to achieve immediate response from e.g. motion sensor, it must be programmed as PG output in Jablotron.
Typical use cases:
Armed status of the house, in order to adjust blinds, heating, cooling and ventilation
Motion sensor to turn on the light in corridor when there is motion at night
Windows in a zone to provide push notification when leaving the house with windows open
In the right top corner, open Menu → Configuration and define PG1 - PG32 as Read-only or Read/Write.
In Service settings of each PG, you can define its device type to adjust icon and configuration.
a. Read-only device types for Reed contacts
b. Read/write device types for Switches
IMPORTANT: It is not possible to combine Jablotron Gateway with any other device on the same bus terminal. All terminals are RS485 standard, but this provides only electric compatibility, not data compatibility.