Water heating or ceiling cooling (heat pump or boiler)
Communication with heat pump is required if TapHome needs to get info about heating or cooling mode. Most of the time heat pumps support Modbus communication protocol.If Modbus is not available potential-free input or output should be used to detect or set the mode. If heat pump has input available, TapHome will command heat pump to switch modes. If output is available, TapHome will be notified by heat pump what mode is currently active.
Besides the heating / cooling mode, communication with heat pump is not required.
Instalaltion company responsible for heating/cooling system needs to guarantee that there is enough flow within primary circuit if all valves are closed. Universal solution is usage of hydraulic switch.
TapHome operates as a thermostat - it provides zone control of temperature.
TapHome output devices switch thermoelectric valves in the heating / cooling manifold. We recommend to lay a cable with multiple wires between the electric distribution box and the manifold to ensure that all valves in manifold will be connected by separate wire plus one common neutral wire. Use 230VAC thermoelectric valves.
FTP data cable is necessary from each room to the electric distribution box. This will serve for connection of temperature sensors and/or thermostats.
Sometime it is necessary to control circulation pump. This needs to be confirmed with company which is delivering heating/cooling system. Circulation pump is controlled by releay output on 12DO module. Relay is turned on every time when at least one valve is opened.
Electric heating (cables, foils, infrared panels)
Before the floor is covered, place Floor temperature sensors with a minimum distance of 1m from the wall.
Run a FTP cable from the electric distribution box to the rooms one by one. One cable runs across all the rooms.
Lay the power cables for heating from the electric distribution box to every room separately.
Check with air conditioning provider which brand and model is being used. There are different solutions available for each manufacturer / model.
The most effective brands to control by TapHome:
LG can be controlled directly via RS485 communication.
FTP cable is necessary to be pulled from distribution box to outdoor unit.
Outdoor unit needs to be fitted by PI485 extension card (availabel on TapHome eshop).
All outdoor units are compatible with PI485 except for the smallest one for 2 indoor units - MU15.
Order shading motors without any remote controls. You will only need a bare motor (e.g. Somfy WT) with four cables - PE, N, Phase up, Phase down.
Lay a separate power cable from every motor to the electric distribution box.
Lay a FTP data cable from shading switches from every room separately to the electric distribution box.
Push buttons for control of blinds should be provided by electrician and not by supplier of shading system to make sure that these buttons are potential free therefore compatible with TapHome. As a side benefit these buttons can be provided in same design as the rest of the buttons/switches in the building.
Make sure one FTP data cable is pulled out on the facade on the edge of south / west side of the house where most of the windows with shading are located.
Lay separate FTP data cable from each wall switch in every room to the electric distribution box.
Lay power cables from the electric distribution box directly to the lights.
Lay a FTP data cable between the electric distribution box and the air ventilation unit.
Preferred communication with air ventilation units is by using Modbus protocol.
Using CO2 sensor is not necessary for control however it delivers information for more precise ventilation. CO2 sensor can be provided by ventilation system or by TapHome.
IP cameras / CCTV
The cameras have to support Onvif communication protocol
TapHome doesn't provide any storage of recordings, just real time stream of video via TapHome app.
The intercoms have to support SIP communication protocol
LAN cable needs to be pulled from router to doorbell. Another cable for powering intercom if it is not powered by PoE.
Some intercoms provide control of gates/doors and lights. If not provided by intercom, two separate wires need to be pulled form distribution box to each controlled device.